Electricity Supply Solutions for an Educational Center in Tanzania
Independent thesis Advanced level (degree of Master (One Year)), 12 credits / 18 HE creditsStudent thesis
The aim of this study was to investigate electricity supply solutions for an educationalcenter that is being built in Chonyonyo Tanzania. Off-grid power generation solutions andfurther optimization possibilities were studied for the case.The study was done for Engineers Without Borders in Sweden. Who are working withMavuno Project on the educational center. The school is set to start operating in year 2015with 40 girl students in the beginning. The educational center will help to improve genderequality by offering high quality education in a safe environment for girls in rural area.It is important for the system to be economically and environmentally sustainable. Thearea has great potential for photovoltaic power generation. Thus PV was considered as theprimary power generation and a diesel generator as a reliable backup. The system sizeoptimization was done with HOMER. For the simulations HOMER required componentdata, weather data and load data. Common components were chose with standardproperties, the loads were based on load estimations from year 2011 and the weather datawas acquired from NASA database. The system size optimization result for this base casewas a system with 26 kW PW; 5.5 kW diesel generator, 15 kW converter and 112 T-105batteries. The initial cost of the system was 55 875 €, the total net present cost 92 121 €and the levelized cost of electricity 0.264 €/kWh.In addition three optimization possibilities were studied. First it was studied how thesystem should be designed and how it would affect the system size to have night loads(security lights) use DC and could the system then be extended in blocks. As a result it wasfound out that the system size could be decreased as the inverter losses would be avoided.Also the system extension in blocks was found to be possible. The second study was aboutinverter stacking where multiple inverters can work as one unit. This type of connectionallows only the required number of inverters to run while shutting down the excess ones.This would allow the converter-unit to run with higher efficiency and lower powerconsumption could be achieved. In future with higher loads the system could be easilyextendable by connecting more inverters either in parallel or series depending on what isneeded. Multiple inverters would also offer higher reliability than using one centralizedinverter. The third study examined how the choice of location for a centralized powergeneration affects the cable sizing for the system. As a result it was found that centralizedpower generation should be located close to high loads in order to avoid long runs of thickcables. Future loads should also be considered when choosing the location. For theeducational center the potential locations for centralized power generation were found outto be close to the school buildings and close to the dormitories.
Place, publisher, year, edition, pages
2013. , 37 p.
Off-grid, Stand-alone, PV, Solar Energy, Solar, HOMER
Environmental Engineering Energy Systems Energy Engineering
IdentifiersURN: urn:nbn:se:du-12805OAI: oai:DiVA.org:du-12805DiVA: diva2:643346